Ymir Water System
Annual Drinking Water Information
Size and number of connections
The system services 107 active connections.
The system is located in the community of Ymir between Nelson and Salmo and is within RDCK Electoral Area G.
The Ymir system currently draws water from an intake located in Quartz Creek. The Quartz Creek area is designated as a Community Watershed. Because of the susceptibility of surface sources to environmental contamination, the system was on Boil Water Advisory from 1995 until 2009, when the new treatment plant was installed.
The system was first constructed in the 1890s to supply water to an expanding mining community. Several stages of upgrades have been performed since that date. The system became a RDCK service in 1979 after a cold winter that froze the entire system and left the community without water for up to six weeks.
A new water treatment plant was installed in Ymir in December, 2009. The plant includes pressurized media filters that are cleaned by a backwash process, 1-micron nominal cartridge filters, and 1-micron absolute cartridge filters. UV disinfection and residual chlorine disinfection provide a microbiological barrier. The plant also uses a SCADA system, which allows for remote monitoring of plant processes. The Ymir Water Treatment Plant has received several awards, including the BC Water and Wastewater Association award for small water systems.
A concrete dam across Quartz Creek provides a small intake reservoir. The system also includes a 273,000 litre steel tank for treated water.
Ymir's distribution system was gradually replaced in a series of recent upgrades. It now includes approximately 4.8 kilometres of PVC pipe.
The system's water pressure and storage capacity meet standardized requirements for fire protection. The distribution network serves 16 fire hydrants. The Ymir water system has been recognized by Fire Underwriters Survey as having a Dwelling Protection Grade since 1986 and has most recently been reviewed in 2014. Subscribing insurance providers can get water system grading information from Fire Underwriters Survey.
In fall 2014, a leak was discovered in the base of the steel water storage reservoir. As a temporary repair a concrete base was cast inside the reservoir but the reservoir will be replaced (see next section).
Plans for future upgrades
The Regional District was successful in obtaining a Clean Water & Wastewater Fund (CWWF) grant in March 2017, in the amount of $642,964! The construction of the 600,000 litre reservoir is in progress, and is projected to be completed in spring 2018.
This system is currently owned and operated by the RDCK. The RDCK receives community-specific advice and policy guidance from the Ymir Water Commission of Management.
The content on this page was last updated April 24 2018 at 12:16 PM